USA, Joined Feb 2010, 2
Concrete Post Inspection
I am looking for a suitable method for inspecting concrete - voids, cracks, delamination.
Self Consolidating Concrete (SCC) will be placed in module between steel plates (1/2 thick plates on either sides). Module dimension = Length-70 Width-44 Height-70. Thickness of concrete inbetween steel plates is approx 2.5.The steel plates will remain as is after construction and it is steel-concrete-steel sandwich structure. The internal has lots of steel pipe penetrations, mechanical connectors, tie rods, interior rebars, pins etc. One of the reason to select SCC is easy flow between these obstructions.
Looking for Post Inspection methods for concrete placed in between using NDT techniques. Most of the methods researched so far cannot be used as the steel plate deflects the signal away. Also no holes or windows can be cut through these steel walls.
Seeking expert opinion on this topic. Appreciate your help.
PRI Nadcap, United Kingdom, Joined Nov 1998, 286
Re: Concrete Post Inspection In Reply to Anu at 23:28 Feb-17-2010 (Opening).
This looks like a tough one.
As you mention, most techniques are not going to work because of the steel plates, but I wonder if some of the aerospace techniques could work when taken to this size.
I am thinking in terms of Thermography or Shearography, but these will depend on the coupling of the steel plates to the concrete.
I take it this is for a future project, so perhaps the design can be slightly modified to better facilitate inspection (such as Studs welded onto the steel plates on the concrete side).
Maybe ask some of the Thermographic and Shearographic people as I don't know enough about them myself to correctly give advice.
The other options could be to introduce sensors into the assembly (inside the steel plates) that would give you the required information. Once again I don't know which type of sensors to recommend.
Consultant, ASNT L-III, Honorary Secretary of BINDT
Level X NDT, BINDT, United Kingdom, Joined Oct 1999, 517
Re: Concrete Post Inspection In Reply to Godfrey Hands at 08:45 Feb-18-2010 .
It's far from a complete solution, But ultrasonic testing from the steel should at least be able, by looking at the echo pattern, to confirm that there is concrete in good contact with it on the far side. This would allow you to at least verify complete fill.
You might be able to check for Gross internal voids by a low frequency through transmission, although the logistical issues would be huge.
Given the scale of the structure its probably worth Mocking Up some test pieces and doing some research to see what could be done.
consultant, Canada, Joined Sep 2006, 821
Re: Concrete Post Inspection In Reply to Joe Buckley at 14:44 Feb-18-2010 .
Just to add my comments to what Godfrey and Joe wrttien. Maybe one technique that could be succesful would be Ground Penetrating Radar. I've seen a show on television and there was also an article in a past issue of the CINDE magasine where they where measuring the thickness of ice on road ice northern Canada.
I don't know anything about it, but that's just a taught.
USA, Joined Feb 2010, 2
Re: Concrete Post Inspection In Reply to Michel Couture at 15:00 Feb-18-2010 .
Thank you all for the valuble comments and suggestions.
@ Godfrey It is for future application but the designer is unwilling to modify the structure. I will look into Shearography which is something I have not come across.
@ Michel We have looked at UT option. It requires access holes on the steel plates to access one face of concrete.
@ Joe GPR does not detect voids, cracks and delaminations, moreover the steel plate will deflect the signal.
Teledyne ICM’s CPSERIES has been designed with a view to
revolutionizing the handling and perfor
mances of portable X-Ray
sets. Despite having managed to halve the weight of similar
portable X-Ray generators available on the market (while
continuing to provide the same power output), the SITEX CPSERIES
generators feature a shutter, a laser pointer, a beryllium window,
an aluminum filter and two integrated diaphragms (customized sizes
are available upon request). Without compromising the robustness
and reliability for which ICM products are renowned, the small
size and light weight of the SITEX CPSERIES will radically change
the way that you perform your RT inspections. And you will see a
positive impact in terms of both quality and return on investment
GEKKO - Portable Phased Array Testing with TFM in Real-Time
The portable phased array testing system GEKKO provides 64 parallel test channels. On creating testi
ng parameters the operator is assisted by the CIVA software. Due to its modular set-up the GEKKO instrument is suitable for operators of all skill levels.
HD-CR 35 NDT Computed Radiography System
Portable high-resolution CR scanner for all radiography applications - weld testing, profile images
and aerospace. No matter what type of radiographic testing you are performing, the unique TreFoc Technology of the HD-CR 35 NDT imaging plate scanner always guarantees the highest image quality.
Exertus Dual 120
The Exertus Dual 120 Projector has the ability to accept Iridium 192
sources or Selenium 75 source
s. This projector incorporates design
safety features that make it flexible, compact and lightweight.
The Projector is lighter than most of its competitors. It
incorporates an improved source channel, based on a new helicoidal
design, which makes maintenance easier. The helicoidal design also
allows smoother movement of the source assembly inside the device,
making it easier for the operator and improving safety. The
Projector also has a unique safety feature not found in competitive
The source assembly locking mechanism is triggered by the source
holder capsule at the front of the source assembly, thereby always
assuring the operator that the source has returned to the
safe position. The Exertus Dual 120 is ISO3999:2004 compliant.